Q&A - RFP Fiber 2019
Diagram to answer question on HS to ES pathwayThe ESPlan3 sheet E 1.01 shows the telecom pathway from in front of the tennis courts leading to the elementary school and then from the elementary school to the high school. The RFP Fiber 2019 google map has the telecom pathway from in front of the tennis courts to a pull-box between the elementary school and high school with conduits going in both directions from that pull-box. I just want to confirm the existing pathway for my proposal.
ESPlan3-SheetE 1.01.pdf is authoritative.
RFP did include some speculative new (not yet existing) pathway possibilities, but they are merely conversation starters.
Proposers are encouraged to determine the best new bored or trenched pathways to meet the project goals.
Yes, HDPE pipe is permitted and is considered a viable conduit. Size shall be determined by proposer based on the segment portion and number of cables that will populate said segment.